Up to 36 kV, up to 25 kA, 1000 A busbar, 630 A and 1000 A feeder
Factory-assembled, type-tested switchgear
according IEC 62 271-200
Customer's Benefit: - Environmental Independence - Compactness - Maintenance-free Design - Personal Safety - Security of Operation, Reliability - Cost-efficient, Ecological
Rated short-duration power-frequency withstand voltage
Rated lightning impulse withstand voltage
Rated peak withstand current
Rated short-circuit making current
Rated short-time withstand current, 1 s
Rated short-circuit breaking current
Rated normal current of busbar
Rated normal current of feeder
630 and 1000*
Degree of protection - Primary part
Degree of protection - Secondary part
Dimensions - Width (Circuit-breaker panel) - Width (Disconnector panel) - Depth with rear duct - Height of the panels
mm mm mm mm
600 450 1000 1900
* Circuit breaker panel with a rated current of 630 A and disconnector panel with a rated current of 630 A and 1000 A
Design and construction
PM (metallic partition)
Loss of service continuity category panels:
Accessibility of Compartments (enclosure):
- Busbar compartment:
- Switching device compartment:
- Low-voltage compartment:
- Cable compartment:
tool-based non accessible tool-based tool-based
Internal arc classification
Designation of internal arc classification IAC for - Wall-standing arrangement - Free-standing arrangement
IAC A FL 25 kA, 1 s IAC A FLR 25 kA, 1 s
Type of accessibility A - F - L - R
Switchgear in closed electrical
service location, access "for
authorized personnel only"
(according to IEC 62271-200)
(for free-standing arrangement)
Arc test current
Please see further details in catalogue (Catalogue can be found under Download).
Arge EGS PPS
E.ON Climate and Renewables
Dalekovod d. d.
res Renewable Energy Systems Ltd.
Enel Green Power S.p.A.
juwi Wind GmbH
Community Windpower Ltd.
Nordex Energy GmbH
Karara Mining Ltd.
Scottish & Southern Energy
Sepisa S.A. de C.V.
EWE Netz GmbH
EDF Energy Renewables
Villeroy & Boch AG