Deutsches Milchkontor GmbH (Dairy)
New construction of a building section for the milk drying plant
Maximum operational safety and flexibility were the key aspects of power supply for the new plant.
For this purpose, power supply is ensured by completely redundant elements in form of a ring supply.
The consumer substation consists of two points of supply: If one of the two medium-voltage substations were to fail, the other one could easily ensure supply of the entire plant.
Planning work was performed – also in regard of future expansions – with the aid of the SIMARIS design and SIMARIS project planning tools.
Products & systems by Totally Integrated Power applied
Consumer substation: 20 kV medium-voltage switchgear and NXPLUS C medium-voltage switchgear
Two 8DJH medium-voltage switchgear substations
Nine GEAFOL cast-resin transformers, 1,600 kVA each
LVMD: Eight SIVACON S8 switchboards incl. 40 panels, their incoming/outgoing feeders equipped with multi-function devices of type SENTRON PAC3200 and PAC4200, whose measuring results are evaluated by a central station.
SD: Five SIVACON S8 low-voltage switchboards for further load distribution
About 550 meters of the SIVACON 8PS busbar trunking system installed in total
WinCC, the process visualization system applied, allows to visualize the energy values of the low-voltage switchboards and monitor the medium-voltage switchgear, transformers, and the low-voltage main distribution system (LVMD).